The views expressed in this page do not represent those of the Planning Inspectorate. This page consists of content submitted to the Planning Inspectorate by the public and other interested parties, giving their views of this proposal.
East Anglia TWO Offshore Windfarm
Received 16 January 2020
From Alan Hatfield
“I am writing to you both to draw your attention to the stupidity of siting a new sub station for the North Sea East Anglia Two and One windfarms in or near Friston. The power generated by the windfarms will far exceed the power required by the homes and businesses near Friston and consequently it will be exported to where it is needed by the National Grid. One of the reasons for choosing Friston was because it had access to the National Grid nearby. However, wherever the power is used, the losses to get it there will be in excess of the benefits of choosing Friston as a site of connection. Let me give an example with the sub station in Friston, consider 1Kw of electricity generated in the North Sea at the new windfarm. This 1Kw will travel say 70km on the Submarine High Voltage Direct Current (HVDC) cable proposed, then be converted to High Voltage Alternating Current at the Friston sub station. This conversion will cause about .7-.8% loss (3). Then the reduced power will travel 160 km on the above ground grid to where it will be used in London. For this example using the figures in National Grids document (1) Resistance is .064(2) Ohms for HVDC and 1.62(2) Ohm for the HVAC circuit, Total 1.68 Ohms. Now consider if the sub station was in the Thames estuary, The same 1 Kw of electricity will travel say 140 km via a new submarine HVDC cable to a new sub station in the Thames estuary. There will be no requirement to bury this cable in 64m wide trenches that pass through an AONB as the cable can be laid on the sea bed. Once at the substation the power can be converted with the same losses (.7%)(3) as in the Friston example and then travel 30km via HVAC overhead to be used in London. The loss figures for this example are Resistance for HVDC 1.28(2) Ohms and HVAC .3 (2) Ohms. Total Resistance 1.58 Ohms. From this example it can be seen that there is a significant saving in power losses and as importantly the destruction to the environment is substantially reduced. From National Grids own document (3) it can be seen that the submarine HVDC is preferred for an even longer route of 385 km. There is a growing need for a strategic plan to site a new UK connector sub station so that subsequent windfarms in the North Sea and International power connectors such as Viking, NueConnect and NEMO (5) can connect to The National Grid near where the power is needed and I would suggest that location should be in the Thames estuary.”